Issue Date: September 11, 1998
April 28, 2005
(originally listed as
Gilbarco Environmental Products and later as Marconi Commerce Systems)
EMC Enhanced, EMC-PC Enhanced,
LMS Environmental Management Consoles with Line
PA0263000100X (Same as Veeder-Root Series 8494),
(Same as Veeder-Root Series 8494)
AUTOMATIC ELECTRONIC LINE LEAK
Leak rate of 3.0 gph at 10 psi* with PD = 100% and PFA = 0%.
Leak rate of 0.2 gph at operating pressure with PD = 100% and PFA = 0%.
Leak rate of 0.1 gph at 1.5 times operating pressure* with PD = 100% and PFA
rate varies as a function of pressure, this leak rate and pressure were
certified using an equivalent leak rate and pressure, in accordance with an
||2.5 gph for leak
rate of 3.0 gph.
0.17 gph for leak rate of 0.2 gph.
0.09 gph for leak rate of 0.1 gph.
A pipeline system should not be declared tight if the test result
indicates a loss that equals or exceeds this threshold.
pressurized fiberglass and steel pipelines.
Tests are conducted at operating pressure.
System will not function with a mechanical line leak detector installed in
||Maximum of 100
delivery and testing.
None between dispensing and testing for leak rate of 3.0 gph.
Minimum of 45 minutes between dispensing and testing for leak rate of 0.2
Minimum of 2 hours between dispensing and testing for leak rate of 0.1
||Response time is
less than 1 minute for leak rate of 3.0 gph.
Response time is 30 to 45 minutes for leak rate of 0.2 gph.
Response time is 32 to 48 minutes for leak rate of 0.1 gph.
Test data are acquired and recorded by a microprocessor.
Calculations are automatically performed by the microprocessor.
installation on pipeline.
Automatic testing of pipeline.
Single test to determine if pipeline is leaking.
Pump shutdown (optional), message display and alarm activation if leak is
||System must be
checked annually and, if necessary, calibrated in accordance with
Midwest Research Institute
125 Powder Forest Dr.
Tel: (816) 753-7600
Simsbury, CT 06070-2003
Date of Evaluation:
Tel: (860) 651-2700