Issue Date: April 18, 1997
Revision Date: March 3, 2009
SIR PRO 1
RECONCILIATION TEST METHOD (QUANTITATIVE)
Horner Products is no longer in business.
Support for this method may not be available.
rate of 0.2 gph with PD > 99.9% and PFA < 0.1% for leak threshold of
Leak rate of 0.2 gph with PD > 97.2% and PFA < 0.1% for leak
threshold of 0.16 gph.
and 0.16 gph for leak rate of 0.2 gph.
These leak thresholds are for evaluation
A tank system should not be declared tight if the test result indicates a
loss or gain that equals or exceeds the leak threshold calculated from the
data set. This leak threshold may be different than the above leak
of 45,000 gallons for single tanks.
Maximum of 45,000 gallons cumulative capacity for manifolded tank systems
with no more than 4 tanks in system.
of 23 days of product level and flow through data.
of data analysis that system employs, and was used during evaluation
process, is exclusive of any external control by vendor.
System consists of a fully automated software package with embedded
algorithms for conducting leak detection testing. Consequently, third
party evaluation procedure demonstrated that system can be used in-house
with no requirement for direct vendor participation.
system was tested for in-house use. Vendor, with evaluator present,
analyzed required data and performed evaluation using program disk only.
Results were presented to evaluator directly from the computer without
additional vendor involvement.
of data sets were from manifolded tank systems.
Of 41 data sets submitted for evaluation, 4 were inconclusive.
Median monthly throughput of tanks evaluated was 22,370 gallons.
Leak rates of 0.05, 0.1, and 0.2 gph were used in evaluation.
Data sets evaluated were supplied by evaluator.
Manufacturer's Previously Listed Contact
Information is No Longer Valid
Tel: (816) 443-2494
Date of Evaluation: 04/07/93,