Issue Date: November 22, 1995
Revision Date: March 3, 2009
SIR PRO 1
Versions 1.0, 2.0
RECONCILIATION TEST METHOD (QUALITATIVE)
Horner Products is no longer in business.
Support for this method may not be available.
||Leak rate of 0.2
gph with PD = 100% and PFA = 0% for Version 1.0.
Leak rate of 0.1 gph with PD = 100% and PFA = 0% for Version 2.0.
||0.1 gph for leak
rate of 0.2 gph.
0.05 gph for leak rate of 0.1 gph.
A tank system should not be declared tight if the test result indicates a
loss or gain that equals or exceeds this threshold.
||Maximum of 18,000
||Minimum of 30
days of product level and flow through data.
||Method of data
analysis that system employs, and was used during evaluation process, is
exclusive of any external control by vendor.
System consists of a fully automated software package with embedded
algorithms for conducting leak detection testing. Consequently, third
party evaluation procedure demonstrated that system can be used in-house
with no requirement for direct vendor participation.
this system for in-house use.
Computer program disk along with
instructional documentation was supplied by vendor to evaluator.
Evaluator, without vendor involvement, analyzed required data and
performed evaluation using program disk and accompanying documentation.
Vendor was present as an observer during evaluation.
using data from manifolded tanks.
Of 120 data sets submitted for evaluation, 10 were inconclusive for
Of 120 data sets submitted for evaluation, 9 were inconclusive for Version
Median monthly throughput of tanks evaluated was 13,640 gallons for
Median monthly throughput of tanks evaluated was 11,828 gallons for
Leak rate of 0.2 gph was used in evaluation for Version 1.
Leak rate of 0.1 gph was used in evaluation for Version 2.
Data sets evaluated were supplied by evaluator.
Manufacturer's Previously Listed Contact
Information is No Longer Valid
Tel: (913) 681-9379
Date of Evaluation: 04/07/93