Issue Date: November 22, 1995
Revision Date: May 21, 2008
Franklin Fueling Systems
(originally listed as INCON Intelligent Controls, Inc.)
AUTOMATIC TANK GAUGING METHOD
||Leak rate of 0.2
gph with PD = 99.9% and PFA = 0.5%.
A tank system should not be declared tight if the test result indicates a
loss or gain that equals or exceeds this threshold.
aviation fuel, fuel oil #4.
||Maximum of 15,000
Tank must be between 50 and 95% full.
||Minimum of 6
hours between delivery and testing. Minimum of 2 hours between dispensing
There must be no delivery during waiting time.
||Minimum of 3
Test data are acquired and recorded by system's computer.
Leak rate is calculated from data determined to be valid by statistical
There must be no dispensing or delivery during test.
product is determined by a minimum of 5 resistance temperature detectors (RTDs).
||Must be used to
detect water ingress.
Minimum detectable water level in the tank is 1.04 inches.
Minimum detectable water level change is 0.011 inch.
||RTDs and probe
must be checked and, if necessary, calibrated in accordance with
using manifolded tank systems. Therefore, this certification is only
applicable when there is a probe used in each tank and the siphon is broken
Tests only portion of tank containing product.
As product level is lowered, leak rate in a leaking tank decreases (due to
lower head pressure).
Consistent testing at low levels could allow a leak to remain
EPA leak detection regulations require testing of the portion of the tank
system which routinely contains product. TS 2000 can support up to 4
Ken Wilcox Associates
3760 Marsh Road
Madison, WI 53718
Tel: (800) 225-9787